Originally Posted by Silock
Gas dude is here now. Just a weird interaction between the water heater venting and the furnace being on that overloads the exhaust vent because of the way the vent tees together, which is why it's intermittent. Only happens when the water heater and the furnace are going at the same time.
He told me how to fix it and is just finishing up. No crazy death traps in the house. Sorry to disappoint!
This is a problem with the DIY type of people. They didn't know to check the sizing of the vent to insure proper ventilation. Glad you got it fixed up.
"Careful not to step in the bullshit."
Every had a Hole In One? I have.
Engineers are always correct!